Welcome to the new forum. We're now hosted on ElectriciansForums.net rather than ElectriciansForums.co.uk - Chat about the forum upgrade by CLICKING HERE
Discuss My 1st board on site advice in the Electrical Forum area at ElectriciansForums.net
Also could you expand a little on B about the cable ties. I used that for aesthetically purposes.A) Proteus is cheap S***
B) You need ferrules on the end of those neutral fly leads.
C) I don't like to see cable ties holding conductors together in a CU
Although at a quick glance aside from the above. Looks ok
Ok so for point B regulations:Also could you expand a little on B about the cable ties. I used that for aesthetically purposes.
The cable tie, is purely my opinion, use them to make it tidy and then I would remove, the cables should have been formed into position.526.9 Connection of multiwire, fine wire and very fine wire conductors
526.9.1 In order to avoid inappropriate separation or spreading of individual wires of multiwire, fine wire or very fine wire conductors, suitable terminals shall be used or the conductor ends shall be suitably treated.
526.9.2 Soldering (tinning) of the whole conductor end of multiwire, fine wire and very fine wire conductors is not permitted if screw terminals are used.
526.9.3 Soldered (tinned) conductor ends on fine wire and very fine wire conductors are not permissible at connection and junction points which are subject in service to a relative movement between the soldered and the non-soldered part of the conductor.